Adjustment item to the value of £1. Useful if adding items to the order...
Brand new 12v 7AH cell, perfect for rebuilding UPS battery banks.These...
Brand new 12v 9AH cell, perfect for rebuilding UPS battery banks.
Brand new 12v 4.5AH cell, perfect for rebuilding UPS battery banks.
Riello 20KVA UPS fully working 90 day RTB warranty.
3 Phase input, and output double conversion pure sine wave UPS.
Tested by us. The existing cell bank ran for 27 minutes at 7.5 KW and we will sell with these batteries at a cheap price. If you would rather buy with new cells, we can quote to replace and fit those before shipping out to you.
Warning: Last items in stock!
Nominal input 380 to 415 VAC (3 phase)
50Hz (40-72 tolerable)
Input voltage tolerance (per phase) 180-264V AC
Input current 38A Max
Output 380/400/415 VAC
Max Power 20KVA / 18KW
Battery compliement 80x 9AH cells.
recharge time ~ 5 hours.
Static variation +/- 1%
Dynamic variation +- 3%
Crest factor 3 to 1
Overload capability at PF 0.8 type load [still best practice is not to overload]
110% for UNLIMITED
125% for 10 minute
150% for 1 minute
Depth 850mm (cables can come out of the bottom of the UPS)
Includes EITHER netman 102 or 204 card, at your choice. We will install this and reset to DHCP IP assignment before shipping. Screenshot taken showing use.
Also includes the original use cables and Mennekes 3 phase (3p+n+E) 63 amp plugs (1x male 1x female), though you could remove these to use existing wiring.
The UPS can be used in online or in economy/smart mode. Economy yields 98% efficiency.
It can be used as a frequency converter, online, eco, smart or standby mode.
No customer reviews for the moment.