Adjustment item to the value of £1. Useful if adding items to the order...
Brand new 12v 7AH cell, perfect for rebuilding UPS battery banks.These...
Brand new 12v 9AH cell, perfect for rebuilding UPS battery banks.
Brand new 12v 5AH cell, perfect for rebuilding UPS battery banks.
APC 3000 XL
rack 3u type
Core only - tested working - 30 days RTB warranty
metal top if they are in short supply
Warning: Last items in stock!
Fully working APC 3000 XL UPS - with 12 month RTB warranty.
New cells installed by us.
2x output leads included.
1x Input C19 lead included.
We ship with everything you need to start using on delivery. Simply plug into the wall power, then attach your devices.
As the unit is an XL type it has provision to add extra cells (48VDC rail) via the rear connector. This can be handy for home energy storage, or for example creating massive run times by attaching to a fork lift truck battery bank.
Max power 3000 VA
Nominal Output Voltage 230V
Output Voltage Note Configurable for 220 : 230 or 240 nominal output voltage
Output Voltage Distortion Less than 5% at full load
Output Frequency (sync to mains) 47 - 53 Hz for 50 Hz nominal , 57 - 63 Hz for 60 Hz nominal
Waveform Type Sine wave
(1) IEC 320 C19 (Battery Backup) ,
(8x) IEC 320 C13 (Battery Backup)
Nominal Input Voltage 230V
Input Frequency 50/60 Hz +/- 5 Hz (auto sensing)
Input Connections IEC-320 C20
Input voltage range for main operations 160 - 286 V
Input voltage adjustable range for mains operation 151 - 302V
Typical recharge time 3 hour(s)
RBC Quantity 1
Communications & Management
DB-9 RS-232 , SmartSlot , USB
LED status display with load and battery bar-graphs and On Line : On Battery : Replace Battery : and Overload Indicators
Alarm when on battery : distinctive low battery alarm : configurable delays
Emergency Power Off (EPO) Yes
Surge energy rating 480 joules
Filtering Full time multi-pole noise filtering : 0.3% IEEE surge let-through : zero clamping response time : meets UL 1449
Please note that the photos will be of either 3000 or 2200va type. The units are phsically the same bar the max power rating.
No customer reviews for the moment.