Test item only. Useful if adding items to the order if we dont have them...
Brand new 12v 9AH cell, perfect for rebuilding UPS battery banks.
Brand new 12v 7AH cell, perfect for rebuilding UPS battery banks.These...
1M 10A lead for plugging devices into your UPS
APC 2200 rmi2u inc New batteries. Fully working. 12m RTB warranty
This unit is incomplete - it does not have the front plastic fascia. This is only a cosmetic issue and does not effect use or performance.
The cell pack is not in the original APC metel tray.
Warning: Last items in stock!
We are offering these as a way of getting the UPS at a reduced price. The photos below show both the original and none original cell packs, and how the UPS looks without its front on.
1x UPS with new batteries / in-house battery tray
1x Input power lead
2x Output power lead
One picture shows the network cards and rails that can be used with this UPS - they are not included.
APC 2200 VA 2u UPS
Manufacturers spec page / docs available
Max Configurable Power 1980 Watts / 2200 VA
Nominal Output Voltage 230V
Output Voltage Note Configurable for 220 : 230 or 240 nominal output voltage
Output Voltage Distortion Less than 5% at full load
Output Frequency (sync to mains) 47 - 53 Hz for 50 Hz nominal, 57 - 63 Hz for 60 Hz nominal
Pure Sine wave
8x IEC 320 C13 output sockets
1x IEC 320 C19 output socket
Nominal Input Voltage 230V
Input Frequency 50/60 Hz +/- 3 Hz (auto sensing)
Input Connections IEC-320 C20
Input voltage range for main operations 160 - 286V
Typical battery recharge time 3 hour(s)
Interface Port(s) DB-9 RS-232, SmartSlot, USB
LED status display with LED's for
load and battery bar-graphs
Emergency Power Off (EPO)
Surge energy rating 480 Joules
Full time multi-pole noise filtering : 0.3% IEEE surge let-through : zero clamping response time : meets UL 1449
Maximum Height 89.00 mm
Maximum Width 483.00 mm
Maximum Depth 660.00 mm
Rack Height 2U
Shipping Weight 54.00 KG
Audible noise at 1 meter from surface of unit 47.00 dBA
Online Thermal Dissipation 400.00 BTU/hr
No customer reviews for the moment.